The Largest Manufacturer of Pipe couplings, Flange Adaptors, Stepped Couplings, Dismantling Joints and related products in the Southern Hemisphere
>> Working Pressure
>> Expansion & Contraction
>> Shear Strength
>> Recommended Bolt Torque
>> Pipe End Preperation
>> Angular Deflection
> Lateral Displacement
>> Ground Settlement
>> Setting Gaps
>> Product Storage
>> Cathodic Protection
>> Anchoring / Supporting Pipes
Fitting Instructions Up to
Fitting Instructions Above 300mm
>> Fitting Ranger Products
>> Material Specifications
Klamflex Ranger and Varifit Products pass SANS 1808-2:2010 test.
Please see attached Test Report
Ranger and Varifit Couplings JASWIC Certificate of Acceptance
PLEASE CONTACT OUR OFFICES FOR DISCOUNTS AND AVAILABILITY
INSTALLING RANGER PRODUCTS
The Coupling is supplied completley assembled.
Start assembling the Coupling on one of the pipes to be joined.
Measure the length of the Coupling and subtract setting gap.
Complete the assembly to finger tight and position Coupling on mark.
Divide the result of the above measurement by two and mark both pipes.
Insert the second pipe to the mark and start tightening.
Dissasemble the Coupling and check all parts.
Tighten bolts - as per KLAMFLEX manual - to recommended torque.
Apply a non-toxic soapy lubricant to the gasket area as shown.
Check gaskets on completed assembly for proper contact and deformations.